6-Inch Product Details & Installation
- Every Hickenbottom® Inlet is made of high-density polyethylene.
- All Hickenbottom® parts, tees, offsets, risers, and inlets snap together for easy installation. Risers and inlets can be cut to desired lengths.
- Markings on Hickenbottom® Inlets allow for easy height adjustment. Find the marking for the desired height and simply cut on the line.
- Hickenbottom® Inlets are lightweight and simple. There is no need to hoist in concrete catch basins and no need to weld aluminum or steel pipe inlets.
- Hickenbottom® Inlets are durable, easy to see, and easily maintained.
- Check out Hickenbottom® adapters to increase or reduce the intake of the inlet off of the inlet’s tee. Contact your local NRCS office to properly size restrictors for your project.
- A special inner riser may be inserted to maintain ponding at a certain level to improve water infiltration in semi-arid regions.
- Hickenbottom® Inlets are government approved. There are authorized distributors in the U.S. and Canada that have inlets in stock for fast delivery to contractors.
General Information for Installation Practices
Installation for all Hickenbottom® Inlets should be in accordance with specifications for corrugated P.E. piping, such as ASTM F-405 and AASHTO highway specifications M-252. These can be found in the Soil Conservation Service Engineering Field Manual for Conservation Practices in Book 2 of 2, Section 8-82 and 8-83.
When back-filling inlets at shallow depths (less than 24 inches), it is recommended that one bed the tee and underground portion of the inlet with 1/2 to 1 1/2 inches of stone aggregate (ie: limey chips). In normal conditions concerning depths less than 24 inches (up to 72 inches), the spoil from the trench may be used for bedding if the size of the spoil material is less than 2 inches in diameter.
In conditions of 72 inches or deeper, one should surround the vertical portion of the inlet with a circumference of approximately 12 inches of the aforementioned aggregate to the surface.
To keep the vertical portion of the inlet from tipping over in the back-filling process, fill around the inlet in a mounding fashion then taper the slope down and away from the inlet to the bottom of the trench.
Make sure that all Hickenbottom® sections are snapped together before backfilling.
Further questions concerning inlet installation may be directed to the general office at 1-800-443-7879.
New Style Tees
- A 6″ tile bell may be fitted over a 6″ SDR.35 bell or a 6″ DR-C900 spigot.
- An HBI-654 reducer may be used to connect a 6″ inlet tee to 6″ field tile. The reducer will fit directly into the bell of the 6″ tee.
- A Hancor 6″ x 5″ reducer (product #FC-R05-06) and 6″ x 4″ reducer (product #FC-R04-06) both fit into a 6″ inlet tee bell.
- Most 6″ reducers work well with this product; however, a piece of 6″ field tile may be needed to connect the tee to the tile.
- The spigot of a 6″ stack may be fitted with all 6″ SDR.35 bell end fittings.
- In order to fit a 6″ Schedule 40 bell over a 6″stack bell, the 6″ stack bell will need to be cut below its rib.
- A Fernco plastic adapter may be fitted to a 6″ stack spigot. Please refer to NCS chart for further flow capacities.